On the surface, the outage that affected northwest Wyoming at about 9:10 a.m. Feb. 23 seems straight forward: A winter storm took down a 69-kilovolt transmission line north of Cody near the Park County Regional Landfill, thrusting the local utilities and the residents of Cody, Powell, Willwood, Garland and Ralston into darkness for nearly two hours.
Power was restored at about 10:50 a.m., but it wasn’t because the downed line was back on the towers.
The evening before, another event about 60 miles away from the downed line, probably caused by wind swinging the cables, called conductors, too close together on the Lovell-to-North Cody 69-kV transmission line, cut off the back-up power feed to the area through the Lovell Substation. This problem left the Big George-to-Glendale Tap 69-kV line the only power source in the area.
“This was a one in a million deal for us,” said Cody Field Manager Doug Padgett, who responded to the Lovell Substation. “You had two separate, distinct problems caused by two separate, distinct events. It was not expected at all.”
Check out the full story on how Western and the local community worked together to restore power in Wyoming at Western’s Newsroom.